Grindmaster Corporation 341A Freezer
Image 1 of 4
Image 2 of 4
Image 3 of 4
Image 4 of 4
If you have any other photos or manuals for the
Grindmaster Corporation 341A you can upload the files here .
The Freezer consists of a freezing cylinder with a rotating internal auger (dasher) that is belt-driven by an electric motor. The auger scrapes frozen product off of the inside of the refrigerated cylinder. Crathco remote beverage freezers are designed to operate in conjunction with a remote condensing unit or be connected to a central refrigeration system. It is recommended that the condensing unit have no more than 2 1/2 hp per barrel to ensure maximum efficiency. The refrigerant must be R404A (Dupont®HP62®). The refrigeration for each barrel is controlled by the liquid feed solenoid. The liquid feed solenoid is opened and closed by the limit switch attached to the drive motor. (When the product consistency reaches the desired point, the switch closes and de-energizes the liquid feed solenoid 20 seconds later.) Twin units operate with each barrel independently. Quick connect refrigeration connections are supplied with each unit. Each Freezer is factory supplied with 5/8" suction and 3/8" liquid connections. The piping connecting the Freezer with the remote condensing unit or central system should be sized according to industry standards. The installer is responsible for sizing the refrigeration lines to the unit. When properly operated and cared for, the remote freezers will provide many years of service. Proper care includes regular cleaning and maintenance. To minimize the amount of maintenance necessary, follow the operating proce- dures outlined in this manual. There are four variations of the remote unit: 3341 – standard single barrel remote unit 3342 – standard twin barrel remote unit 3341A – single barrel remote unit with internal autofill system 3352 – dual barrel remote unit with internal autofill system
Service and User Manual
859.40 Kbytes (880025 Bytes)
2000 01 01
Electronic document, no scan, very well readable.
2016 12 28
Introduction ... . ... . ... 2 Freezer Application & Specifications ... . ... 2 Installation ... . ... . ... 15 Operation & Adjustments ... . ... . ... 7 Care and Cleaning ... . ... . ... 8 Maintenance ... . ... . ... 12 Troubleshooting ... . ... . ... 15 Key Parts Identification ... . ... . ... 16 Assembly & Wiring Diagrams (3341/3341A) ... . ... 17 Assembly & Wiring Diagrams (3342/3352) ... . ... 26 Autofill Connections Guide ... . ... . ... 35
Terms and Conditions
These terms and conditions contain rules about posting comments. By submitting a comment, you are declaring that you agree with these rules:
- Although the administrator will attempt to moderate comments, it is impossible for every comment to have been moderated at any given time.
- You acknowledge that all comments express the views and opinions of the original author and not those of the administrator.
- You agree not to post any material which is knowingly false, obscene, hateful, threatening, harassing or invasive of a person's privacy.
- The administrator has the right to edit, move or remove any comment for any reason and without notice.
Failure to comply with these rules may result in being banned from further commenting.
These terms and conditions are subject to change at any time and without notice.